View and Download Hach Sc E instrument manual online. Analysis System. Sc E Measuring Instruments pdf manual download. Hach Sc Controller User Manual – Download as PDF File .pdf), Text File .txt) or read online. Hach Sc Controller User Manual . Hach Company, – .. 37 W with 25 W sensor/network card load 24 VDCpowered sc model: 24 VDC.
|Published (Last):||21 December 2005|
|PDF File Size:||7.81 Mb|
|ePub File Size:||4.61 Mb|
|Price:||Free* [*Free Regsitration Required]|
All configuration settings and calibrations can be changed. Calibrate Sensor as required by regulatory agency Per agency-dictated schedule.
Page 26 Installation 3. Table of Contents Add to my manuals Add. Choose a number between 1 and as the address each source must have a different address then press ENTER.
Hach sc100 1720E Instrument Manual
Do not touch the new bulb with bare hands. Theory Of Operation General Information 2. Section 7 Troubleshooting 7. Don’t see a manual you are looking for?
In the event that a defect is discovered during the warranty period, Hach Company agrees that, at its option, it will repair or replace the defective product or refund the purchase price, subject to the pro-rated schedule above, excluding hachh shipping and handling charges.
Warranty, liability and complaints 7. Restore sample flow to the instrument. Mounting The Controller Installation 3.
Close and secure the cover. In the United States: Drain body and clean the body and bubble trap.
Pipe vertical or horizontal 5. To hold the output until released: The warranty period for instruments is 24 months. Failure to do so could result in serious injury to the operator or damage to the equipment. Haach attention to all danger and caution statements. The passcode is factory set to sc the five digits must be followed by a space to remove the trailing asterisk.
Page 51 Modbus Protocol Table 9: Operation During calibration, analog outputs can remain active, held, or transferred to a preset mA value. Section 7 Troubleshooting Section 7 Troubleshooting 7. Page 37 Operation 4. Section 4 Operation Section amnual Operation 4. Disconnect and remove the existing wires between the quick connect and terminal block J5, see Figure 21 on page 4.
Remove the quick connect fitting and wires and install the threaded plug on the opening to maintain the environmental rating. Page 30 Operation 4. Page 50 Modbus Protocol Table 9: Under normal use, Hach recommends replacing the lamp once a year to maintain peak performance. Table of Contents Section 1 Specifications To print the manual completely, please, download it.
Twist the bulb in a counterclockwise direction, pulling out slightly, until it is released from the housing. Installation Figure 8 Panel Mounting the Controller 1 2 3 4 5 6 7 8 9 8 10 11 1. Setting Up System Security Operation 4. Measured reading ssc100 on a gain of 1. Section 1 Specifications Section 1 Specifications Specifications are subject to change without notice.
Page 10 General Information 2.
Hach-Lange SC : Owner manual
Page 18 Installation 3. Customize ssc100 outputs using the table in section 4. Section 2 General Information 2. Close and secure the cover.
Fuses F1 and F2. Controller Dimension Illustrations Installation 3. DEADBAND—Sets the range where the relay remains on after the measured value decreases below the setpoint value high phase relay or increases above the setpoint value low phase relay. Section 4 Operation 4.
Supporting test records by Hach Company, certified compliance by Hach Company. Relays K1, K2, and K3. Dc100 14 Installation 3. Relay loads must be resistive. By pressing ‘print’ button you will print only current page.
Seat hah against connector with no bare wire exposed. The display will flash on startup, when a sensor error has occurred, when the hold outputs function has been activated, and when a sensor is being calibrated. Page 21 Installation 3. Section 10 Repair Service Authorization must be obtained from Hach Company before sending any items for repair.